How do I prepare for and manage loss of power to my display or control system?
- How do you prepare for and manage loss of power to your display or control system?
- Product Family: Control System, Video
- Control System:
- This article explains recommended procedure to prepare for and manage power loss. If power is lost in your facility, there are steps that can be taken in your off-season and during an event to minimize potential damage to your display(s) and Daktronics control systems. Following these steps will help your system recover quickly once power restores. Daktronics recommends facilities to have a back-up plan in place for power failure occurrences. Every site is different, so having a plan in place will help reaction time and allow systems to be better maintained.
Off Season Preparation
The following steps can be performed during your off-season to help your site be better prepared for an unexpected power outage during an event.
- Verify Uninterruptible Power Supply (UPS) Systems
- Verify that all critical control equipment is attached to UPS units.
- These units should be loaded to manufactures specs, but generally no more than 50% of their stated capacity.
- These will need to be replaced every 2 - 3 years to maintain full runtime in the case of an outage.
- Make sure to back up all data and files before running this test. Shut down any equipment you know is not running on a UPS.
- Schedule a time with facility operations to turn off the utility power supply and switch to alternate power (if applicable). This will give you an opportunity to test all standby power systems and make sure all UPS units are functioning properly.
- Practice the steps below (Start with Power failure to Display or Scoreboard) to insure you are prepared for an event time power outage.
- Make note of any equipment that is or is not powered as you expected. If your facility has auxiliary power, make note of which outlets and equipment are functioning while utility power is disconnected.
- Shutdown and power off all control systems and displays before returning to utility power.
Managing Display or Scoreboard Failure
- If the power outage impacts your display during an event, it is recommended to power off the following components:
- Video displays
- Auxiliary displays
- Pro-Ad or ribbon board displays
- Fixed digit scoreboards.
- Turn your Remote Power Switch (if applicable) in your rack to the OFF position.
- Turn power off to your display(s) and scoreboards at the circuit breaker.
- Turn display and scoreboard power back on at the circuit breaker
- wait :30 - :60sec before turning the circuit breakers on as there may be power spikes while all major facility components (Lights, HVAC, etc.) come back online.
Managing Control Room Power Failure
- If there is a power failure inside your control system rack and you have uninterruptible power supplies (UPSs), your rack will run long enough to shut down unnecessary components for maximum work time. This will give you enough time to:
- Save all open content, close open applications
- Perform a shutdown of all computers not in use
- If time allows, run back-up software one last time from your back-up computers
- Power down VIPs, A/B Switches, Signal Converters
- Note: If you lose power in your control room ONLY and your display is still functioning, it is recommended to shut down non-essential components to give UPS units their maximum usage while power is being restored. Non-essential equipment may include but is not limited to:
- Back-up computers
- Back-up VIPs
- Signal converters
- Rack-mounted mouse, monitor, and keyboard
- If you do not have UPS units inside your rack, unplug rack mounted power strips killing power to all components until power is restored.
- Begin restoring power starting with any VIP (Video Image Processors) and working up to your computers (Venus 7000, Venus 1500, and/or Show Control). For more information on proper Power up and Shutdown procedures, refer to What is the proper rack startup procedure?, DD2308283.
KB ID: DD3100708
DISCLAIMER: Use of this content may void the equipment warranty, please read the disclaimer prior to performing any service of the equipment.
DAKTRONICS DOES NOT PROMISE THAT THE CONTENT PROVIDED HEREIN IS ERROR-FREE OR THAT ANY DEFECTS WILL BE CORRECTED, OR THAT YOUR USE OF THE CONTENT WILL PROVIDE SPECIFIC RESULTS. THE CONTENT IS DELIVERED ON AN "AS-IS" AND "AS-AVAILABLE" BASIS. ALL INFORMATION PROVIDED IN THIS ARTICLE IS SUBJECT TO CHANGE WITHOUT NOTICE. DAKTRONICS DISCLAIMS ALL WARRANTIES, EXPRESS OR IMPLIED, INCLUDING ANY WARRANTIES OF ACCURACY, NON-INFRINGEMENT, MERCHANTABILITY AND FITNESS FOR A PARTICULAR PURPOSE. DAKTRONICS DISCLAIMS ANY AND ALL LIABILITY FOR THE ACTS, OMISSIONS AND CONDUCT OF YOU OR ANY THIRD PARTIES IN CONNECTION WITH OR RELATED TO YOUR USE OF THE CONTENT. ADJUSTMENT, REPAIR, OR SERVICE OF THE EQUIPMENT BY ANYONE OTHER THAN DAKTRONICS OR ITS AUTHORIZED REPAIR AGENTS MAY VOID THE EQUIPMENT WARRANTY. YOU ASSUME TOTAL RESPONSIBILITY FOR YOUR USE OF THE CONTENT AND ANY LINKED CONTENT. YOUR SOLE REMEDY AGAINST DAKTRONICS FOR DISSATISFACTION WITH THE CONTENT IS TO STOP USING THE CONTENT. THIS LIMITATION OF RELIEF IS A PART OF THE BARGAIN BETWEEN THE PARTIES.
The above disclaimer applies to any property damage, equipment failure, liability, infringement, or personal injury claim arising out of or in any way related to your use or application of the content, whether such claim is for breach of contract, tort, negligence or any other cause of action.